# What is a touch voltage?

## What is a touch voltage?

The term touch voltage refers to the shock hazard present on any exposed metalwork or protective conductor. The voltage exists if there is a higher resistance earth path to the exposed metalwork than to the ground beneath your feet or another piece of exposed metalwork in close proximity, as shown in figures 1a & 1b.

## How is touch voltage calculated?

Next, from the value of the calculated potential difference between the earthing system (GPR=fault current multiplied by earthing resistance) and the point on the surface where the person is standing (VS), touch voltage (UTp=GPR–VS) is calculated as the voltage on the voltage divider – 1) human body (according to IEEE …

## What is the maximum permissible touch voltage?

This value of 50 V is known as the conventional touch voltage limit (UL).

## Why does 50v touch voltage?

The 50 V AC conventional touch voltage limit relates to the requirements of Section 411 of IET Wiring Regulations for protection against electric shock in a TN system in the event a fault between a line conductor and earthed exposed-conductive-parts or a protective, under healthy network conditions.

## What causes touch voltage?

Touch voltages are liable to occur between simultaneously accessible exposed-conductive-parts and extraneous-conductive-parts in an installation, particularly under conditions of fault within the installation.

## What is touch current?

The definition of touch current in 60950 is “electric current through a human body when it touches one or more accessible parts”.

## What is touch potential?

Touch potential is the voltage between any two points on a person’s body – hand to hand, shoulder to back, elbow to hip, hand to foot and so on. For example, if an overhead conductor falls on a car, and a person touches that car, current could pass from the energized car through the person to the ground.

## How is touch potential calculated?

1. Resistance reading (R) = 0.2Ω
2. Fault current (I) = 1000 Amps.
3. Touch potential (V) = R*I =
4. 0.2*1000= 200 Volts.

## How does bonding reduce touch voltage?

main protective bonding will generally reduce touch voltages by the value of voltage drop across the conductor acting as earth return in Ze so obviously the benefits will be keenly felt when that part is of higher impedance and the fault current is high.

## What is the safe voltage for a human body?

The safe voltage is the voltage that does not cause a physical shock, generally less than 36 volts.

## How do I stop touching potential?

Multi-grounded neutral helps to reduce the dangerous step potential and touch potential during line-to-ground faults. By creating low impedance path back to the source, faults are quickly cleared by fault interrupters. Multiple grounding electrodes tied together helps to reduce the touch potentials at the fault point.

## What is a safe touch voltage?

The safe voltage is the voltage that does not cause a physical shock, generally less than 36 volts . A safe voltage is a voltage that does not cause direct death or disability. The “safety extra low voltage” that allows continuous contact under normal environmental conditions is 24V. (may also be 36V, 12V AC/DC, 24V is the most common)

Touch-Potential – Touch potential is a potential difference between the fingers of a raising hand touching the faulted structure and the feet of the person standing on substation floor.

## What is a voltage controller?

Voltage controller. A voltage controller, also called an AC voltage controller or AC regulator is an electronic module based on either thyristors, TRIACs , SCRs or IGBTs , which converts a fixed voltage, fixed frequency alternating current (AC) electrical input supply to obtain variable voltage in output delivered to a resistive load.